Products > Other Pumps > Acid and alkali resistant chemical pump
Acid and alkali resistant chemical pump
Release time:2019-02-28  Browse times:879
boiler electric motor 380v FRPP material plastic acid proof chemical pump
When applied to heat-exchange, install a pressure gauge at the outlet to ensure no blockage in the pipeline.
A strainer should be installed at the inlet to revent solids from being sucked in.
Install valves at the inlet and the outlet for easy maintenance.
Strainer mesh should be dia. 5~7mm and total mesh area is 5 times the pipe area or more.
1. Different chemical solutions mixed together will cause reaction and even heat to damage the pump. Don't pump different chemical solutions with the same pump.
2. Chemicals may cause serious injury. Keep away from dangerous area.
3. Before operating, please check the discharge and suction line and valves
rst. Make sure valves are all in correct position, then start. During
operation, check discharge usually.
4. Incorrect operation, for example, valves closed, incompatible material and
dry running may cause dangerous. Especially dry running, it will cause heat
as well as vapor, even some chemical decomposes hydrogen and explode.
5. Start the pump and check the discharge from the outlet. If it is too low,
unplug the pump immediately, and check the pipeline if there is any block..
6. The pump can be equipped with explosive-proof and pressure-proof motor.